Compressor: Enclosed scroll rotary compressor with high efficiency, low noise, less leakage, and maintenance (compared with semi enclosed or piston compressor) has the advantages such as the power from 4 to 13HP, fewer moving parts with damping, and liquid resistance device.
Evaporator: The evaporator area is increased and the enthalpy difference is increased to 0.95 to improve the efficiency of heat exchange。 The surface of the evaporator through non stick water coating surface treatment technology is decreased the condensed water on the surface of the residence time, and meets the international standard of ASTMD572799 to solve the problem that the condensed water into air heat exchange more efficient. The efficiency ratio of heat transfer is up to 1:4.
Fan: The world's original radial direct fan is based on the principle of the jet engine. The impeller fan is used the new type of eddy current, reverse rotating blades, suction and exhaust running at the same time to improve the efficiency of the air supply. Because of the use of oil-bearing fan and dynamic and static balance correction, the noise greatly reduced. For the 20-level speed control fan, the air pressure can be from 50PA to 450PA. The user can adjust the corresponding pressure according to the distance of air supply in the room. The farthest distance of air supply is up to 150 meters. The fan is located in the central of air conditioning. The lower part of air conditioning is used as the plenum noise in order to avoid the bottom blowing directly to the ground caused by air turbulence。 The air pressure is adjustable in the field with ranging from 20Pa to 230Pa to meet a variety of environment。 To compare with belt type fan, the transmission is more efficiently – loss negligible, low noise and less vibration, less maintenance - not necessarily periodic replacement of the belt and the necessary belt adjustment。 The belt grinding dust will flow (extremely harmful to the machine and personnel) into the room.
Heater: The electric heater has the perfect overheating protection function and anti ionization, and there are various heating methods (water heating or electric heating) for the base station of small heat load in high cold area that can meet the requirements of the environment。
Humidifier: The electrode type humidifier is the repeated disassembly and cleaning. The humidifier adopts advanced fuzzy intelligent control with automatic adjustment of water level and detection of current according to the different scale of humidifying and the flushing rate. The electrode type humidifier should be cleaned and replaced in the field. Humidifier can be repeated use and long term use. The humidifying pot with the green material can be dissolved。 The humidifying capacity is 9kg/h (can also be adjustable according to the needs of users). It includes the automatic cleaning sewage capacity and the maintenance convenient disassembly. The advantage of electrode type humidifier is high efficiency which is over than 90% and high humidity control precision that has fast response time to adapt to the general water quality. Comparison of infrared humidifier, the infrared humidifying efficiency is lower than 60% and has slow response time。 The replacement parts of infrared humidifier are very expensive and there are certain requirements on water quality. Comparison of ultrasonic humidification, the ultrasonic humidification is generated aerosol on equipment and easy to cause harmful bacteria.
Dehumidification: It has quick dehumidification including dehumidification solenoid valve with special structure to reduce the thermal compensation and the power consumption of air-conditioning dehumidification process。
Humidity controller: It adopts the absolute humidity of advanced energy saving control mode。 According to the absolute humidity to adjust relieves the room temperature fluctuations in the relative humidity change which causes the unnecessary missed operation increasing the power consumption.
过滤器： 10000粒/升。高效的灰尘粒子浓度过滤网达到国际G4标准,能保证机房的洁净度达到A级机房的要求(直径大于0.5) 。
Filter: 10000 grains / L。 The efficient concentration of dust particle filter is reached to the international G4 standard, and can guarantee the room clean degree reach A class room requirements (diameter greater than 0.5).
Condenser: The condenser casing is used the corrosion resistant alloy to ensure the service life and appearance。 With external rotor type axial flow fan is designed to meet the requirements of environmental protection and noise reduction. Fan speed is controlled according to different environmental temperature to ensure good operation effect and energy saving。
Control system adopts advanced microprocessor to provide more accurate operation precision. The temperature control precision is ± 0。2 ℃, as well as humidity control precision is ± 5%. Using HIROMATIC intelligent (touch) graphics controller can provide 20 pages and 60 strips status report (7 languages can be selected including Chinese). Low power operation automatically executes during the night and holidays to reach the energy saving and prolong the service life of equipment。 Up to 128 networks and a variety of networking monitoring can realize the real-time remote for the air conditioner. Control system with multiple password protection is used to against accidental operation. The system supports the local network, the remote network, building automation system, power and environment monitoring network.
HIMOD network control has two ways。 The standard model is used the MICROFACE。 Since each system is equipped with MICROFACE, using the HIROBUS control bus can be up to 16 machines together。 MICROFACE has the functions as follows:
The temperature and humidity control.
LCD screen displays the corresponding parameters.
The password protection prevents the change of parameters.
The standby machine rotates. The system consisting of multiple machines in general has a plurality as the standby machine. In order to prevent the backup machine in a long waiting state, the HIMOD can set the rotation time. The backup machine works automatically when the time is set, and other working machine turns to backup state as the moving circles.
This chart is for reference only, the new design of components and structures for the unit will change depending on the actual situation。